Type of Document Dissertation Author Skolthanarat, Siriya Author's Email Address email@example.com URN etd-09092009-020426 Title The Modeling and Control of a Wind Farm and Grid Interconnection in a multi-machine system Degree PhD Department Electrical and Computer Engineering Advisory Committee
Advisor Name Title Centeno, Virgilio A. Committee Chair De La Ree Lopez, Jaime Committee Member Kohler, Werner E. Committee Member Liu, Yilu Committee Member Wang, Fei Fred Committee Member Keywords
- dynamic modeling
- harmonic distortion
- grid interconnection
- Wind energy
Date of Defense 2009-08-26 Availability unrestricted AbstractThis dissertation focuses on the modeling and control of WECS (Wind Energy Conversion System) in a multi-machine system. As one of the fastest growing renewable energy resources, the trend of wind energy changes to variable speed wind turbines. The concept of the variable speed is based on the variable speed according to the instantaneous wind speed of wind turbines. Since the utility grid requires the stable frequency and magnitude voltages, there must be grid interconnection of the wind farm and the utility grid. The grid interconnection must support the concept of the variable speed wind turbines. Since each wind turbine locates in a different location in a wind site, it receives the different wind speed. Hence the grid interconnection must convert the variable frequency and magnitude output voltages of the wind turbines to a synchronous frequency and magnitude voltages associated to the grid.
With the new technologies of power semiconductor devices, the power converter can operate with high voltage, high current, and high switching frequency. This results in a higher power capacity of a wind farm. Nonetheless, the power converters generate harmonic distortions to the utility grid. The harmonic distortions components in the voltages and currents of the grid degrade the power quality. This results in the damage of electrical components in the power system such as capacitor banks, inductors, protection devices, etc. The harmonic distortions can be reduced with the technology of the multi-level inverter. It is required that the wind energy provides the real and reactive power control for frequency and voltage stability. In order to achieve the power control, the modeling and control of the power electronic grid interconnection is presented in this dissertation.
The grid interconnection is modeled with linearization techniques. The models in frequency domain in the form of transfer functions are used to design the compensators in the control system. The model is considered as a SISO (Single Input Single Output) system to design the compensators in SISO tool of MATLAB. The selected control system is current control that can control the real and reactive powers independently. Furthermore, since the grid interconnection is modeled separately for each sub-system, the control system is verified with integration of the sub-systems. The grid interconnection is modeled in Simulink and simulated in the PSCAD.
In reality, the power system is comprised of multi-machines. They affect the power system stability, reliability, and quality. The dynamic modeling of an aggregated wind farm with synchronous generator and grid interconnection in a multi-machine system is presented. The test system is a 10-bus system with three generators and three loads. The dynamic modeling involves the power flow calculations that determine the equilibrium points of the system. The system is modeled with differential equations of wind turbines, synchronous generators, and grid interconnection. The system is modeled in the time domain in state space form. The system characteristics can be determined by poles or eigen values obtained from the characteristic equations. Since the system is MIMO (Multi Input Multi Output) system, the optimal control theory is used to reduce the deviation of system behaviors during disturbances. The LQR (Linear Quadratic Regulator) is utilized to control the system with eigen value assignment method. Simulation results in Simulink are illustrated.
Filename Size Approximate Download Time (Hours:Minutes:Seconds)
28.8 Modem 56K Modem ISDN (64 Kb) ISDN (128 Kb) Higher-speed Access Skolthanarat_S_D_2009.pdf 2.42 Mb 00:11:11 00:05:45 00:05:02 00:02:31 00:00:12
If you have questions or technical problems, please Contact DLA.